I have been looking into options for a z-wave/zigbee thermostat to integrate my home heating (no cooling at this stage). Initially I was going to await the integration of Nest thermostats but with my many Aeotec Multisensor 6's around the house, I thought why not utilize these with a simple z-wave switch to control the on and off of the central heating and then eventually smart ducts or in line valves in the ceiling to zone the house. My system is only a 2 wire control so this should be easily handled.
I realize there will be quite a few rules to handle this but why not complete all the scheduling and far more advanced rules than a thermostat has all in Hubitat?
Has anyone tackled similar?
It would be nice to have this as a separate rule machine type app specific for whole house temperature control within the Hubitat.
Thanks @JohnRob. I am in Australia. My system is a natural gas central heating and currently this is single zone only. Not sure where you are located but AU systems tend to be quite basic and a simple on and off command that is controlled via temperature. For example, my thermostat is programmable for 4 changes per day for each of the 7 days. It is battery operated and has 2 wires to the main heating unit. I believe the main unit supplies 24VAC on one of the wires and it is switched by a battery operated relay in the thermostat via temperature (similar to below). The main heating unit simply receives the 24VAC signal and self controls the ignition, gas and fan.
Adding cooling to a unit will change to a three wire control:
This should be easily controlled but yes agree on the conservative approach, just cant wait for the Nest integration.
We have a small warehouse facility in Scottsdale, Arizona, divided between some office space and a warehouse space. The warehouse space has both an evaporative cooler and a heat pump for cooling or heating. This time of year, we are in cooling mode.
The evaporative cooler has a simple on/off control. I linked a ST multi-sensor to Rule Machine, and a z-wave relay wired into the low voltage control for the cooler. RM easily handles this automation. Once the temps here got to above 40° C, the evaporative cooler no longer could keep up. So, I installed a Zen Thermostat to replace the existing thermostat that controls the heat pump.
Now, using Rule Machine I have a two stage cooling system. When the temperature is in the range that the evaporative cooler works, the heat pump is disabled by setting the Zen thermostat to off. Once the temperature rises above that range, the evaporative cooler is turned off, and the Zen set to cooling mode. This is done with a single rule, so it can move back and forth between the two stages. I suppose there is some loss of efficiency due to the evaporative cooler introducing humidity, and the heat pump extracting that humidity. However, I'm sure that the overall energy usage is reduced by using the evaporative cooler as much as possible, and only resorting to the heat pump when it's very hot.
Rule Machine is fine for this because I'm using a single multi-sensor. To use several multi-sensors one would need to write a small app to average their temperatures, and present that through a child virtual device. Hardly seems worth the effort to write an entire app devoted to this application -- it is just a cobbled together thermostat: a sensor and a switch.
Perfect option of switching between the two cooling sources for efficiency @bravenel. I will look at similar between my split system heat pumps (electric) and the gas heating once I get a whole house energy monitoring device. This will be aimed at reducing my electricity consumption from the grid and rely further on the produced solar power. At the moment Aeotec don't supply an AU version (921.45mhz) smart energy meter.
Agree that standard temp control is far too much work for no added benefit.
Thanks @napalmcsr for the threads. I will look into theses.
Cheers for all your comments and opinions on this subject, most helpful.
here is an app that allows creating rules for temperature management. turning on a thermostat to cool or heat a house is already built-in to the app. but it does not currently handle a two stage solution like @bravenel described using evaporative cooler and heat pump or heat pump and gas heating in your case.
if you are interested in giving the app a try i would be happy to extend the app to support two conditional cooling/heating sources based on temperature (and power usage) range.
I ported my average temp device driver and little app to Hubitat a long time ago if you need it.
I wrote it to average out a couple of indoor/outdoor temp devices in my conservatory to help control my windows.
Has worked reliably for some months
Let me know if you would like a copy of the code and I’ll post it on github
I ended up getting a Zen Thermostat that has been working perfectly. I have a RM rule for mode change (Heat/Off) based on presence with a virtual button to override off. I also then have a rule setup for each of the day modes which sets temperature. ie day mode (20degC) evening mode (22degC) and night (16degC). This has been working very well with no issues.
I updated to the latest 126.96.36.199 which seams to have caused issues with the communication to the Zen. Thus far it appears that RM is doing it thing correctly but the Zen is not receiving the communication. I have had to manually set the temp or Mode a number of times now on the Zen. Would this be an issue with the latest update or a coincidence @patrick . I have not yet removed and repaired the Zen to see if this helps but certainly don't want to do this on every update.
I checked my Zen and it also was not responding to change in setpoint automations. Only after I enabled debug logging and saved did it respond. A voice command of "I'm hot" or "I'm cold" should throw a virtual switch which triggers a setpoint adjustment of + or- 1 degree. The virtual switch turned on but I do not have any events logged for the actual rule that changes setpoint. FWIW, that rule was built with the old version of RM and I'm on .118.
I also turned on debug logging and it seamed to work then. Will monitor the performance and advise of any changes. Cheers for the response.
I am a google home user so would have to use IFTTT, but how did you handle the rules for increase in temp by voice command?
So far it is working. I didn’t really get time to investigate the increase/decrease in temp.
My temp changes on mode and previously it was very responsive. Now it does seem to have a delay. I have not had enough time to investigate logs on this one yet but will as soon as time permits.
I just checked and all my zen thermostat rules are already 2.5’s
Also upgraded to 118 last night.
This is interesting. I tried my voice command adjustment again and only the heatingSetpoint was changed. It took four attempts to manually adjust the coolingSetpoint from the device page. I'm going to play with this a little more, but right now I'd say something is wrong.
Also I have a bypass to manually turn off the Zen if not required. I have this virtual button on the dashboard and the below shows it was on which should not bypass the rule (this virtual button is in the restrictions of the Thermostat mode change rule above):