Hi guys @bravenel and @bcopeland , I apologize if this was brought up elsewhere but after searching and reading a lot of threads I cannot find an answer. I'm running a brand new T6 thermostat with the built in T6 Pro driver and the TStat scheduler app. I'm using 'modes' for setting the setpoints and the setpoints from the scheduler app are not getting applied to the thermostat. The device screen and dashboard work just fine it's just when the scheduler attempts to change the setpoint.
I had the logs turned on and everything looks like it should be working but one thing I noticed is that the scheduler uses a decimal setpoint instead of an integer. When I adjust the SP with the device page or dashboard the logs indicate setCoolingSetpoint(xx) and T6 responds right away with the new setpoint (the reply is decimal but not the command), When the scheduler does it the logs indicate setCoolingSetpoint(xx.x) which the T6 ignores and never acknowledges. I think the T6 does not like the setpoint command as a decimal as that's literally the only thing different in the logs. Is this something you've maybe seen before or can check to see if the decimal is a problem? I can't see any other difference in the logs. Thanks!